Description

Feature

Splice and terminate cables, emergency overload temperatures up 266°F (130°C)

Poly-isobutylene (PIB) tape

Physical and electrical properties are unaffected when the degree of stretch

Self-fusing（Adhesive）tape

Liner not stick on tape

Compatible with all solid dielectric cable Insulation as Polyethylene, XLP, PVC, Butyl Rubber, EPR and Oil-based rubber

Application

Primary electrical insulation for splicing cable from 600 V to 15kV on all solid dielectric cables

Primary insulation for building stress cones up to 10kV on all solid dielectric cables

Medium-voltage splices Jacketing and terminations

Moisture sealant electrical connections

Bus bar insulations

End sealing high-voltage cables

Color

● Black

Dimension

Width Thickness Length 19mm（3/4 in） 0.76mm（30mils） 9.15m(30 ft) 25mm (1 in) 0.76mm（30mils） 4.5m(15 ft) 38mm (1.5 in) 50mm (2 in)

Package

● 100 PCS/Carton

Specification

Index Typical Value Test Method Tensile Strength 1.86 MPa ASTM D 4325 Elongation 769% ASTM D 4325 Di-electric Strength 32.9kV/mm ASTM D 4325 Di-electric Constant 2.82 ASTM D 4325 Self-adhesion Ⅲ Pass ASTM D 4388 Heat Exposure(130℃/168H) Pass ASTM D 4388 Ozone Resistance Pass ASTM D 4325 Ultraviolet Radiation Aging Pass ASTM D 4325 Xenon Lamp Aging Pass ISO4892-2 Normal Temperature 90℃（194℉） Emergency Temperature 130℃（266℉）

*All these data are typical value

Warranty & Storage

● 5-year shelf life from date of manufacture

● 10°C/50°F to 27°C/80°F storage temperature

● <75% relative humidity